The couple had had their crawl space encapsulated back in 2008. So they called to have it checked due to hearing weird noises. Michael, our service tech found that the Sump Pump was full of mud, and sediments were lodged in the pipes preventing the water to be discharged out of the crawl space causing slight flooding of the pump. Giving us a perfect example of why yearly check-ups are recommended.
our service area